The FP0842 Alarm Acknowledge Module provides a facility to locally annunciate a smoke/CO detector alarm, and for the occupant to acknowledge and clear a false fire alarm without the fire brigade being called.
The AAM4 with an inbuilt sounder is usually installed in a single occupancy unit (apartment, flat or single-person’s quarters) along with 1 or more non-latching smoke/CO fire detectors. When an alarm is detected the inbuilt sounder and red LED in the AAM4 operate and the occupant has (typically) 30 seconds to acknowledge the alarm. This starts a further time delay (typically 1-3 minutes), during which they must clear the smoke to avoid calling the fire brigade If either time delay elapses and smoke is still present, then the fire panel goes into alarm and the brigade is called.
The AAM4 is compatible with the MX4428/F4000 and Simplex 4100 FIPs.
– Operating Voltage 18-28Vdc
– Quiescent Current 0µA
– Alarm Current (max) 23mA Sounder On
– Alarm Current (max) 15mA Sounder Off
– Operating Temperature -5°C to +45°C
– Operating Humidity 10% to 95% R.H (n/cond)
– Weight (typical) 100g
– Approvals FTS-136
– Time Limit Panel Programmable